Circuit Breaker Panel
A circuit breaker panel is the main point from where electricity is passed around to other electrical circuits. Power for your house comes through the service entrance which passes through the electrical meter which records the amount of voltage you use. It then flows through the circuit breaker panel. The panel usually gives out 100 to 200 amps of power. The panel, in short, is just a bunch of switches.
The service entrance wires are attached to terminals called lugs. Lugs are always energised with electricity unless your local power company shuts it off. A dead front cover, which is a metal panel, covers all the lugs and electrical wiring connected to the panel. The dead front cover provides access to every breaker and switch.
The circuit breaker panel always consists of a main breaker which is a large switch. If the main breaker is shut down, then electricity access to every other circuit is cut off as well. However, the lugs remain energised with electricity. Main breaker activity does not affect the lugs. The circuit breaker panel always has two rows for the branch circuits. It includes circuits which provide 15-20 Amps of energy for lighting or fans or other outlets in a kitchen or garage. Branch circuits which are labelled with 40-50 amps of energy are known as ‘double pole breakers’. These supply electricity to high voltage appliances such as dryers or air conditioners. A large breaker may also supply electricity to a sub-panel which is mainly used for electricity in detached r quarters. The panel also has hot & neutral bus bars. Moreover, the ground wires prevent electrocution from happening due to frayed hot wires. Many circuit breakers also consist of disconnectors.
A circuit breaker disconnector is used to isolate the electrical circuit from electricity to maintain or repair it. A disconnector is only used for safety purposes and can be operated either manually or automatically. Circuit breaker disconnectors are off-loading devices which means that they do not contain the workings for controlling electric arcs and should be opened after the current is interrupted by another device.
A circuit breaker disconnect consists of a lock-out tag-out that prevents inattentive operations from happening. These locks are part of a trapped-key interlock system so that there is steady stream of operations. A switch disconnector combines the properties of a disconnector and load switch.
In disconnecting circuit breakers, the disconnector is integrated so that there is no need to use separate disconnectors. This has the advantage of being reliable and the need for maintenance decreases. The usage of this device is, however, limited as compared to a disconnector because there may be problem which arise while maintenance takes place.
A fused disconnect is used to replace a circuit breaker as it works in the same way and is cheaper. It can turn a circuit on or off and its fuses can provide protection. Having more information about electrical breakers and disconnectors can help you in every-day life. If a small electrical problem was to arise, you’d be able to solve it yourself.
Learn more about J & P Electrical Company and their vast line of new, surplus, and refurbished industrial electrical components including: circuit breakers, bus ducts, bus plugs, disconnects, fuses, panel switches, tap boxes, and transformers at www.jpelectricalcompany.com. To contact one of our product reconditioning specialists, call 877.844.5514 today.